The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What is required to convert a Heavy Duty Safety Switch to use Class J fuses?
Heavy Duty Safety Switch
Field assistance with conversion
Need to understand how to convert
Provisions for installing Class J fuses are included in 30A - 400A, 600V and 100A - 400A 240V, fusible Heavy Duty safety switches. Conversion to Class J spacing requires relocating the load side fuse base assembly (or assemblies, as applicable) from the standard Class H fuse location to an alternate position as marked in the switch enclosure. Switches rated 600A, 240V or 600V, require the addition of an adapter kit, catalog number H600J.