Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
What is the part number for a 1600A or above disconnect switch in a NEMA 3R enclosure?
QED 2, BP switch
Design and product availability
Product will need to be configured as a N3R switchboard with a Bolted-Pressure switch.
This can be done using QuoteFast, EQM, or product selectors. Contact your local distributor for a quotation.
Be sure to confirm the system voltage because a ground fault relay is needed for a 480/277v switch for service entrance.