Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Conduit entry allowed to Ventilated and Non Ventilated Transformers
Applies to Ventilated and Non Ventilated Transformers by SquareD/Schneider Electric
Ventilated and Non Ventilated Transformers have an allowable wiring area, below the terminal strip, shown on the CAD drawing
Yes, Customer can punch holes in the bottom pan and conduit stub-up to it as needed. The left and right front sides of the transformer enclosure, below the terminal strip are also an allowable area. Conduit entry is restricted to the crosshatched wiring area shown on the CAD drawing.