The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Conduit entry allowed to Ventilated and Non Ventilated Transformers
Applies to Ventilated and Non Ventilated Transformers by SquareD/Schneider Electric
Ventilated and Non Ventilated Transformers have an allowable wiring area, below the terminal strip, shown on the CAD drawing
Yes, Customer can punch holes in the bottom pan and conduit stub-up to it as needed. The left and right front sides of the transformer enclosure, below the terminal strip are also an allowable area. Conduit entry is restricted to the crosshatched wiring area shown on the CAD drawing.