The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What causes an internal fault on the ATV66 drives?
The +15vdc and - 15vdc power supplies are below +/- 11.5vdc
Before making any voltage checks make sure you have removed mains voltage from L1 L2 and L3 and install single phase voltage (mains power) into CL1 CL2 minus any jumpers.
Check the +/- 15vdc supplies on J9 connector pins 3, 4 and 5
Pin 4 is 0v
Pin 3 is -15vdc
Pin 4 is +15vdc
if any of these voltages are below +/- 11.5vdc you will get the internal fault code.
Possible problems: can be
LEM's or CT's might be shorting out power supplies
Shorted gate driver boards
Shorted or inoperative power board