Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Can a 90degC conductor be used in a switchboard?
75degC cables are generally used if there are not any 100% rated devices in the switchboard. If there are 100% rated devices then 90degC should be used and sized to 75degC cable capacity.
See bulletin 2700DB0203 through Google.