Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
During secondary injection the breaker is only indicating half of the injected current.
NW Frame Breakers
FFTK testing a NW breaker.
This will happen when a W frame (standard width) breaker is being tested as a Y frame (double-wide) breaker. The FFTK defaults to testing as a Y frame.
To get a good test, on the setup screen where you select breaker type, choose NW40b or test as an IEC breaker. This will force it to recognize it as a W frame and test it correctly.