Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The secondary fuse of the control transformer is blowing.
S-Flex 21, S-Flex 212, E-Flex, M-Flex
All models and serial numbers
Caused by short circuit to ground. Possible loose wire or defective or damaged contactor coil.
Trace short circuit with ohm meter. Replace coil if necessary.