...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
The secondary fuse of the control transformer is blowing.
S-Flex 21, S-Flex 212, E-Flex, M-Flex
All models and serial numbers
Caused by short circuit to ground. Possible loose wire or defective or damaged contactor coil.
Trace short circuit with ohm meter. Replace coil if necessary.