Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Can a 2 pole breaker be installed in a new NQ panel with a B phase high leg?
Breaker installation in panel
Yes, when phased to A and C phases, a 2 pole breaker can be installed in a new NQ panel with a B phase high leg.