The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Do you have to select a shunt trip coil for a Powerpact P or Masterpact NT/NW breaker when they're electrically operated?
Q2C Product Selector
Not sure what features you are getting while in product selector.
A shunt trip is a necessary selection.In product selector for electrically operated Masterpact breakers. The selector will give you separate selections for shunt trip, closing coil, and spring charge motor, and you may choose different control voltages for each.
Powerpact P frame
In product selector you only choose the option "Spring Charge Motor". This will automatically give you a shunt trip, closing coil and spring charge motor, all the same control voltage. Everything is included in this option, so if you were to select a shunt trip, it would be a second shunt trip. You will also notice there is no option given for a closing coil.