Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Where do you terminate the load side conductors to the 9065 motor logic solid state overload relay in the NEMA size 00, 0, and 1 8536 starters?
Full Voltage starters NEMA style, Solid State overload relays
8536, 9065 motor logic
Run the conductors from the motor up through the CT's on the bottom of the 9065 solid state motor logic overload relay,
Terminate the conductors to the bottom of the contacts labeled T1 T2 AND T3 located at the bottom of the contactor.