The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The DJM32400E20 tenant circuit breaker in a 400A EZML or EZMK, Series M02, needs to be replaced.
Power Pact Circuit Breaker
EZM Meter Center
The DJM32400E20 has been obsoleted.
A replacement for the obsolete DJM32400E20 is needed.
The DJM32400E20 can be replaced with the LJL36400U31X. A mounting kit, S36967, is also required. The lugs on the OFF end of the LJL36400U31X must be removed to allow for connection to the busbars. When the EZML branch is a single phase device, the B phase (center) lug should also be removed from the ON end of the breaker.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!