Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Can compression lugs be used on Powerpact P frame and R frame I-Line breakers?
Powerpact P frame and R frame circuit breakers
I-Line panels and switchboards only
Customers have reason to use compression lugs and there are conditions to using them.
Yes, they can be used, but in panelboards they require use of an End Gutter Box Extension.
Compression lugs extend beyond the load end of a circuit breaker and an end gutter or side gutter box extension is required to meet electrical code wire bending requirements.
When a factory-assembled panelboard with compression lugs is specified in Quote-to-Cash, the Panelboard Product Selector will automatically configure the necessary box extension(s).
I-Line panelboards are cULus listed with mechanical or compression lugs.
See product data bulletin 2110DB0901.