Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Where is a remote start/stop contact wired to the SFlex 212 drive?
For an S-Flex that does not have the bypass option, wire a dry contact between the field terminals P24 and F.
For an S-Flex that has the bypass option, there was a design change 1/2013 that changed the control circuit. Consult the S-Flex labelling to determine the design.
The earlier version has the run contact wired to field terminals P24 and F. This is in the 24Vdc control circuit.
The later version has the run contact wired to field terminals 5 and 6. This is in the 120Vac control circuit.
In all cases, a contact closure runs the drive and opening the contact stops the drive. For units with bypass option, the selector switch needs to be in AFC.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!