The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Is a LAL36400MB with a short handle required instead of a LAL36400 as the main breaker in a 400a NQ or NQOD panel?
NQ or NQOD 400a
No, either could work. The door on the trim will close when the handle on LAL36400 is in the on or off position. If the breaker trips with the door shut the handle might slightly push on the door when the free-to-trip mech works but that shouldn`t cause any real problem.
CTA-ID : 2055009