The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Controlling Drive with N2 with start stop and speed reference.
F108 is 0
F807 =1 terminal wiring or 0 for RJ45
F829= 2 N2 setup
F851= 4 network fault setup
F890= 1 thru 3 for addressing
F892= 300 for a 30 sec time out
To start the drive via network.
Binary output point 3 is CMD
Analog output point 1 is speed freq reference
Monitor status and speed
Binary input point 6 is ETA run status
Analog input point 1 is output speed
For monitoring only everything else the same as above.
FNOD= 1 for VIA or the customer can choose.
CNOD= 0 for terminal start stop
Wiring on Terminals
+ is B terminal
- is A terminal
Ground is GND terminal
Shield is SCR terminal