Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
|Network Management Card||
|Call-UPS II Out of Band Management SmartSlot Card||AP9608||Second highest||Second-highest-numbered slot (highest if no network management card is present)|
|Dry Contact I/O SmartSlot Card||AP9610
|Medium||Any slot numbered lower than a network management card, Call-UPS II; any slot higher than Measure-UPS|
|Interface Expander SmartSlot Card||AP9607||Medium||Any slot numbered lower than a network management card, Call-UPS II; any slot higher than Measure-UPS|
|Measure-UPS SmartSlot Card||AP9612T
The following graphic is an example of how to install multiple SmartSlot devices in the Symmetra Power Array. Please note the numbering shown in the figure. The network management card is installed in slot #4, Call-UPS II in #3, Interface Expander in #2, and Measure- UPS in #1.
The following graphic is an example of how to install multiple SmartSlot devices in the Symmetra RM and Symmetra LX. The network management card is installed in slot #2 and Call-UPS II is installed in slot #1.