Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Cable size allowed
The wire range is 4 - 3/0 - 500 kcmil al or cu. However the actual lug range is (4) 3/0 - 750 kcmil al or cu. If the wire range required is larger than 500 use the NEC table to determine how many inches of wire bending space is required. Add the required wireway to the panel to allow for the extra wire bending space.
CTA-ID : 2059530