Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Design for single phase
Because there are 3 poles on the busbar, main breaker I-Line panels always use 3 pole breakers, whether single phase or three phase. For single phase panels, only A and C phases are connected to the utility power. The B or center phase is used only as a spacer.
CTA-ID : 2053706