Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Is there a two pole version of the Powerpact D and Powerpact L frame breaker?
Powerpact Breakers, Unit Mount and ILINE Breakers
Products sold in North America
Need a 2 pole breaker in the 400 A to 600A frame size.
The breaker only come in 3 and 4 pole versions, but the 3 pole breakers can be used in two pole applications just use the outer poles.
For more information on the Powerpact L frame consult PowerPact™ H-, J-, and L-Frame Circuit Breakers Catalog 0611CT1001.
The Powerpact D frame is currently being obsolete. The availability is limited.