Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Certain applications call for an Isolated Ground System
Applies to Transformers by SquareD/Schneider Electric
Isolated Ground (IG) Systems are sometimes specified to reduce transient noise and ground loop currents
Contractors are sometimes required to create an isolated ground, or IG system at the Transformer secondary. Many installers have conceptual problems with IG systems. Some think that it means that the secondary neutral is not grounded, others interpret that a separate ground bar is required in the Transformer. Neither of these are correct. To originate an IG ground wire at the Transformer, simply carry a separate, IG ground conductor from the equipment ground point in the Transformer to an isolated ground bar in the secondary panel.
The isolated ground and the equipment ground originate from the same ground point within the Transformer, where they are bonded to building ground, but remain separated in the panel and in all branch circuits.
The purpose of isolated ground is to provide a single point ground for all load point receptacles, rather than the multiple grounds and potential ground current loops associated with a traditional, daisy chained equipment ground schemes.
It is thought that IG systems provide improved resistance to load equipment disturbances caused by ground loop currents and common-mode transients.
The minimum requirements for isolated ground systems are outlined in the National Electrical Code. Further information can be found in the IEEE 1100 Emerald Book on grounding sensitive electronic equipment.
CTA-ID : 2050165
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!