The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Buck and Boost Transformers often appear to be too small for the large loads they carry
Applies to Buck and Boost Transformers by SquareD/Schneider Electric
Buck and Boost Transformers carry only a small percentage of the total load
Applications for Buck & Boost Transformers consist of wiring the Transformers as Autotransformers. Autotransformers are physically much smaller than isolation Transformers, depending on the percent voltage change between input and output. The less percentage difference between input and output voltage, the smaller the Autotransformer physical size can be in relation to it`s output kVA capacity. Typical Buck & Boost applications make small changes in voltage. For example, a 5% change in voltage can be done with an Autotransformer that is 1/20th the size of a comparable isolation Transformer.
CTA-ID : 2049472
Sign up for all the latest solutions, offers and best practices straight to your inbox.