Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Current Transformers require shorting blocks to be used when they are being installed or serviced
Applies to Current Transformers (CT's) by SquareD/Schneider Electric
Current Transformers can produce very high voltage potentials at their secondary terminals if disconnected when primary current flow is present
Current Transformers must never be open-circuited when current may pass through their window. Catalog # 3090TB4 for 4 pole and 3090TB6 for 6 pole shorting blocks used with CTs. The hazard of electric shock, burn, or explosion exists on an open circuited CT. Death, severe personal injury, or equipment damage can result if the leads are touched when the CT is open-circuited.. As much as 4000V on the secondary has been measured on large core CTs with an open-circuited secondary. CTs must ALWAYS be shorted or connected to a burden such as a meter or relay, it must be demagnetized or accuracy may be reduced.