Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
No, a K frame breaker will not fit into an HCN panel. If the panel is wired to 480v , the largest branch available is a 150a H frame.
If wired to 240v the largest is a Q frame breaker up to 225a
CTA-ID : 2044606