The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Clearances vary with type of Transformer installed
Applies to Low Voltage Transformers by SquareD/Schneider Electric
Transformers produce heat in operation, so must have clearance to obstructions
Older, non-EE Ventilated dry type Transformers must be installed so that a minimum of 6 inches clearance is available between a ventilation opening and any wall or other obstructions. Energy Efficient Transformer require a minimum of 3`` clearance from ventilated openings. This does not apply to bottom ventilation openings. Non-ventilated Transformers should be a minimum of 3 inches from any obstruction on all sides and top. Epoxy resin filled Transformers may be mounted directly on the wall, but require 12 inches on both sides, top and bottom. Unit substation style Transformers require a minimum of 12 inches around the ventilation openings, and local codes may exceed that. The clearance requirement is clearly marked on the nameplate of the Transformers.
CTA-ID : 2044982