Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Allocation of space for Ventilated Transformer installation
Applies to Ventilated Transformers by SquareD/Schneider Electric
Ventilated Transformers require clearance space between the top surface of the enclosure and any obstruction for proper heat dissipation
There should be at least 36 inches of clearance between the bottom of the top Transformer and the top of the bottom Transformer.
(NOTE: this information does not apply to EX transformers. Presently, the clearance required between stacked EX has not been determined).
CTA-ID : 2038518