...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Allocation of space for Ventilated Transformer installation
Applies to Ventilated Transformers by SquareD/Schneider Electric
Ventilated Transformers require clearance space between the top surface of the enclosure and any obstruction for proper heat dissipation
There should be at least 36 inches of clearance between the bottom of the top Transformer and the top of the bottom Transformer.
(NOTE: this information does not apply to EX transformers. Presently, the clearance required between stacked EX has not been determined).
CTA-ID : 2038518