Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Clearance requirements for Transformers from external obstructions
Applies to EE type LV Transformers by SquareD/Schneider Electric
Transformers radiate heat when in operation, which must be dissipated
Older Transformers had specified a 6 inch clearance from any obstruction from the front and rear ventilated opening. The EE Transformer clearance has been reduced to 3 inches of clearance from any obstruction from the front and rear ventilated opening.
CTA-ID : 2035671
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!