The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Do you need to take into consideration the service factor of the motor when setting the trip range on the Solid State Motorlogic overload relay?
Solid State Overload relay
Micrologic Solid State Overload Relays
If the continuous - rated motor has a service factor of 1.0, then you would set the dial to 90% of the motor's full load current.
Otherwise, there is a built in service factor of 1.15 - 1.25. If the continuous - rated motor has a service factor of 1.15 - 1.25,
set the dial to the motor's full load current rating. All other service factor ratings will need to be calculated by others.