The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Local and National Codes may require grounding/bonding of the neutral on a Transformer Secondary
Applies to Low Voltage (LV) Transformers by SquareD/Schneider Electric
The neutral terminal on the Transformer Secondary is not physically grounded/bonded when the Transformer is shipped
Neutral bonding can be done either at the Transformer or, in certain circumstances, in the secondary panel. Since neutral bonding should never be done at both the Transformer and the secondary panel, Square D/Schneider Electric does not bond the neutral in the transformer. If the installer chooses to bond ground within the Transformer, they should locate and install a neutral ground lug on the enclosure at a location that is physically convenient for the required bonding to a legitimate building ground, whether it be cold water pipe, structural steel or driven ground rod.
CTA-ID : 2034840