Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Many loads used in Industrial and Commercial applications can generate harmonic energy which may be harmful to standard Transformers
Applies to Ventilated type Transformers by SquareD/Schneider Electric
K rated Transformers are available as a possible solution to the problem of harmonic energy that might damage a standard Transformer
K-Factor is a measure of current distortion in the load fed by a Transformer. The higher the number, the greater the capacity of the Transformer to handle high levels of continuous single-phase, line-to-neutral non-linear loads. Square D/Schneider Electric recommends K-4 rated Transformers for computer and other similar loads found in commercial and industrial systems for duty cycles (24 hour average loading) of 80-95%. If the duty cycle is expected to exceed 95%, then K-13 would be needed. For duty cycles up to 50%, use Type EE energy efficient Transformers. For duty cycles of 50-80%, use Watchdog Low Temperature Rise Transformers.
The need for K-Factor rated Transformers is currently in question because standard, general purpose Transformers can supply typical commercial and industrial `non-linear` loads up to more than 80% of nameplate rating without overheating. Studies have shown that typical loading of low voltage dry Type transformers is less than 35% as a daily average.
CTA-ID : 2033144