The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Most three phase Transformers have Delta primaries, with no neutral
Applies to LV Transformers by SquareD/Schneider Electric
Delta Primaries are inherently more stable
SquareD/Schneider Electric provides Wye primary on Delta secondary with center tap Transformers (T151 voltage code). The primary of this unit does not provide a terminal for a neutral. Connecting the primary of a Transformer to the neutral point of a Wye system can cause troublesome neutral currents during times of imbalance. Generally, it is best to select a Delta primary for most 3 phase applications, even when connecting to a Wye power system. Other than the T151 voltage code design, no wye primaries are offered by SquareD/Schneider Electric.
CTA-ID : 2031542