Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Most three phase Transformers have Delta primaries, with no neutral
Applies to LV Transformers by SquareD/Schneider Electric
Delta Primaries are inherently more stable
SquareD/Schneider Electric provides Wye primary on Delta secondary with center tap Transformers (T151 voltage code). The primary of this unit does not provide a terminal for a neutral. Connecting the primary of a Transformer to the neutral point of a Wye system can cause troublesome neutral currents during times of imbalance. Generally, it is best to select a Delta primary for most 3 phase applications, even when connecting to a Wye power system. Other than the T151 voltage code design, no wye primaries are offered by SquareD/Schneider Electric.
CTA-ID : 2031542
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!