Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Application on 3w system
Use 4w panel on different voltage
Yes, ONLY if the panel is being fed from a 480Y/277 V system upstream and they are simply not pulling the neutral conductor to the NF interior. 2 pole breakers can be used.
Note: The NF panel CANNOT be used on a 3ph, 3w delta system. The EDB or similar branch breakers are not rated for 480 V to ground.