Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Issue:With a 480V primary, 0.5A fuses are recommended, with a maximum rating of 0.52A permitted using the 250% rule of NEC450.3. The fuses are to be
Applies to Industrial Control Transformers by SquareD/Schneider Electric
Overcurrent protection is often required for Industrial Control Transformers
1-1/2 x 13/32`` Class CC rejection type, 600V maximum, time delay fuses (Bussmann Type FNQ-R or equivalent). Qty (2) are required. On the 120V secondary side, a 1.25A fuse is recommended, with a maximum rating of 1.39A permitted according to the 167% rule of NEC 450.3. Provisions are for qty (1) fuse, which must be 1-1/2 x 13/32``, non-rejection type fuse (Bussmann type FNQ or equivalent).
CTA-ID : 2031382