The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Issue:With a 480V primary, 0.5A fuses are recommended, with a maximum rating of 0.52A permitted using the 250% rule of NEC450.3. The fuses are to be
Applies to Industrial Control Transformers by SquareD/Schneider Electric
Overcurrent protection is often required for Industrial Control Transformers
1-1/2 x 13/32`` Class CC rejection type, 600V maximum, time delay fuses (Bussmann Type FNQ-R or equivalent). Qty (2) are required. On the 120V secondary side, a 1.25A fuse is recommended, with a maximum rating of 1.39A permitted according to the 167% rule of NEC 450.3. Provisions are for qty (1) fuse, which must be 1-1/2 x 13/32``, non-rejection type fuse (Bussmann type FNQ or equivalent).
CTA-ID : 2031382