Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Yes, the main breaker kit should remain in place so the panel will utilize the same box and trim. The following will be required per panel:
(1) NFALM2 Main Lug Kit for Series E1 interiors only . Customer to supply and get a fabricated closing plate for the breaker opening.
CTA-ID : 2029995