Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Certain specifications may call for Plenum Rated Transformers
Applies to all Low Voltage Transformer Products by SquareD/Schneider Electric
Nonexistence of a specific Plenum Rating for transformers
First, there are no plenum rated transformers. Here's why:
Section 300.22(B) of the NEC 2005 states that ``Equipment or devices shall be permitted in such ducts or plenum chambers only if necessary for their direct action upon or sensing of the contained air`` Obviously a transformer doesn`t fit that requirement since the transformer is not heating or moving or sensing the air.
But wait! There`s hope. Section 300.22.(C). covers ``Other spaces used for environmental air`` (such as ceilings). Sub Section (2) states that ``Electrical equipment with a metal enclosure....shall be permitted to be installed in such other space....`` Since our transformers have the metal enclosure they can me mounted in the Other space (but not the plenum)
The caveat to Section 300.22.(C).(2) is Section 450.13 (A) which states ``Dry-type transformers 600 volts nominal or less and not exceeding 50 kVA shall be permitted in hollow spaces of buildings ...provided they meet the ventilation requirements of 450.9 and separation from combustible materials requirements of 450.21(A)``
CTA-ID : 2026621