Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Electrical Distribution Equipment
Connect the control wires of proper voltage to the UVR terminals under the accessory cover. Route the wires out the top of the cover through knock-outs.
Constant voltage at the correct level for the device (24V, 120V, AC, DC, etc) should be applied to terminals numbered D1 and D4. Designation for UV trip is MN.
Link to instruction bulletin 48940-22-01:
CTA-ID : 2025182