Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Using taps on backfed Transformers
Applies to Transformers by SquareD/Schneider Electric
Backfeeding on Transformers must be done with recognition of certain limitations
Taps are placed on the primary side of a Transformer to compensate for poor (other than nominal) incoming voltage, allowing the Transformer to operate at it`s designed magnetic flux levels in the core. When backfeeding the Transformer, the magnetic flux level in the core cannot be optimized, since the secondary which is now being fed has no taps to adjust. When backfeeding, it is best to not use the taps on the primary set at anything but nominal (rated) voltage level.