Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
All MCCB and Masterpact circuit breakers
IR scans often contain images and verbiage indicating problems with the installation when no problem exists.
Thermal scans are best used as a preventative maintenance tool. The breakers should be benchmarked (preferably early in their service life), and subsequent tests at periodic intervals (typically annually) should be compared with the benchmark to see if anything has changed significantly. If so, investigate the cause. If these readings are within limits, and the breaker shows no evidence of overheating (discoloration, nuisance tripping, smell, etc.) record the reading and monitor to see if it changes over time.
For isolated scans (snapshots), a common practice is to compare the temperature of a breaker with the temperatures of similar breakers with similar loading. All temperatures should also be below the UL limits:
UL Surface Temperature Rise Limits
Non-metallic 60 deg. C
Metallic 35 deg. C
UL Terminal Temperature Rise
80% Rated CB 50 deg. C
100% Rated CB 60 deg. C
SEE ATTACHED for more information
If any breakers with similar loading are significantly warmer than others, the cause should be investigated. It is possible to have loose or high-resistance connections on either the line or load side. Check the wire torque--and check for discoloration and odors which would be a sign of excessive heat.
The way thermal scans are presented often needlessly alarms the customer. Colors on the scans are relative, so look at the numbers. Also, have an experienced third-party review the scan if there are recommendations for replacing breakers that have moderate temperatures and no signs of overheating other than the colors on a thermal scan.