The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What is a QMB334TW?
QMB panelboard, switchboard with QMB distribution.
Products sold in the United States.
The QMB334TW was a device designed for use with Class T fuses on a 480Y/277V system (see next paragraph for more history on this device). This device is now OBSOLETE. The substitution would be a QMJ364T, which uses Class J fuses, and is a 3-pole device.
HISTORY: The QMB334TW was designed for use with Class T fuses on a 480Y/277 Vac system. The 1990 National Electrical Code (NEC) 240-60(a) exception permitted this application. The wording in the 1993 NEC 240-60(a) exception was clarified to support the proper application of a 300 Volt type fuse ``in single-phase line-to-neutral circuits supplied from 3-phase, 4-wire, solidly grounded neutral systems where the line-to-neutral voltage does not exceed 300V.`` 300 Volt type fuses are permitted only when applied in accordance with NEC 240.60(a). As the device is now obsolete, consider using a 3-pole QMJ364T (uses Class J fuses) for this application.
CTA-ID : 2008592
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!