The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes. I-Line main lug panels can be rotated in the field to accept top or bottom feed.
NOTE: Rotating the interior will affect the location of larger breakers (wide side only) on HCW / HCP, HCWM and HCWM-U / HCR-U. On a bottom feed interior, the ``wide side`` is on the left of the bus stack. On a top feed interior, the ``wide side`` is on the right side of the bus stack.
CTA-ID : 438