The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes. I-Line main lug panels can be rotated in the field to accept top or bottom feed.
NOTE: Rotating the interior will affect the location of larger breakers (wide side only) on HCW / HCP, HCWM and HCWM-U / HCR-U. On a bottom feed interior, the ``wide side`` is on the left of the bus stack. On a top feed interior, the ``wide side`` is on the right side of the bus stack.
CTA-ID : 438
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!