The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Center tap capacity of a center tapped delta secondary
Applies to Transformers with center tapped delta secondaries by SquareD/Schneider Electric
Center tap capacity must be limited based on Transformer design factors
Delta-Delta connected Transformers are intended to supply balanced three-phase loads, such as motors. Unbalanced loading will cause a circulating current to flow in the windings. This additional current is like a ``hidden`` load with the Transformer windings and can severely de-rate or even overload the Transformer. Adding a center tap on the secondary for a combination of a 240V three-phase and 120V single-phase loads will exacerbate the effect in a more severe imbalance. In older design Transformers by SquareD/Schneider Electric, such as those with catalog numbers ending in T6HCT, the amount of the imbalance was limited to 5% to help prevent excessive circulating currents. Newer designs, such as the EE75T151HCT, have a much higher, 30% limit to loading on the center tap. See below attachment for more details.
CTA-ID : 2001190