Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
9070T , E
Heat contribution information can be obtained from LVGP Product Marketing/Support. Its also on p.25 of 9070CT9901 for the 9070T products . If the full load losses of the transformer are known, then the heat contribution at full load can be obtained by multiplying the loss in watts by 3.414 to yield BTU/hr. If the information is critical, it should be requested each time from Product Marketing as transformer designs are subject to change without notice.
Example: From Product Marketing/Support, the full load losses of the 9070T2000D1 is 132 watts. Multiplying by 3.414 yields a heat contributiion at full load to be 451 BTU/hr.
CTA-ID : 2000572