The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
9070T , E
Heat contribution information can be obtained from LVGP Product Marketing/Support. Its also on p.25 of 9070CT9901 for the 9070T products . If the full load losses of the transformer are known, then the heat contribution at full load can be obtained by multiplying the loss in watts by 3.414 to yield BTU/hr. If the information is critical, it should be requested each time from Product Marketing as transformer designs are subject to change without notice.
Example: From Product Marketing/Support, the full load losses of the 9070T2000D1 is 132 watts. Multiplying by 3.414 yields a heat contributiion at full load to be 451 BTU/hr.
CTA-ID : 2000572