Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Transformer types intended for different purposes must be chosen carefully, even if the basic electrical requirements for which they are needed are satisfied
Applies to SquareD/Schneider Electric Sealed Resin Epoxy Encapsulated Transformers and Ventilated Transformers
Different Transformer types having similar electrical characteristics can have dissimilar physical features
An encapsulated transformer has the core and coil surrounded by an epoxy resin and sand encapsulation material, which is baked, effectively becoming a ``brick`` that is locked into the enclosure, effectively sealing out moisture and contaminants from the core and coil. Heat removal from the transformer is only provided through the surface of the enclosure. The encapsulated transformer utilizes a Class 180 insulation system with a standard temperature rise of 115degC. This is the principal method used in manufacturing small transformers (below 15kVA.) It is not as popular at higher KVA ratings because of the higher cost, greater weight, and lower impedance than comparable Ventilated Transformers. Square D/Schneider Electric can provide Sealed Resin Epoxy Encapsulated Transformers 0.05 KVA through 25 KVA single phase, and 3 KVA through 30 KVA three phase. As well, Sealed Resin Epoxy Encapsulated Transformers are offered as wall mounted, with no wall clearance required beyond that provided by the mounting provisions. They do require 12 inches of clearance around the sides and top to allow for sufficient air circulation to remove the heat from the surface of the transformer (this requirement is clearly marked on the nameplate of the transformer in accordance with UL requirements).
Ventilated Transformers have the core and coil enclosed by a steel enclosure except for ventilation openings. Air circulates around the core and coil and is removed primarily through the ventilation openings. Newer, Energy Efficient (EE Type) Transformers require 3 inches of clearance around the ventilation openings (this requirement is clearly marked on the nameplate of the transformer in accordance with UL requirements.) Older, Non- Energy Efficient Transformers require 6 inches of clearance around the ventilation openings.
The Ventilated Transformers typically utilize a Class 220 insulation system with a standard temperature rise of 150degC. This is the principal method used in manufacturing transformers 15kVA and larger. It is more popular than Sealed Resin Epoxy Encapsulated Transformers at these higher KVA ratings because of the lower cost, lower weight, and better impedance than comparable Sealed Resin Epoxy Encapsulated Transformers. Square D/Schneider Electric can provide Ventilated Transformers 15kVA through 500kVA single phase (UL up to 167kVA,) and 15kVA through 2500kVA three phase (UL through 1000kVA.)
CTA-ID : 15961
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!