The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Taps provided on Transformers may be adjusted to provide for different Primary input voltages
Applies to all Transformers with taps supplied by SquareD/Schneider Electric
Supply voltages for Transformer Primaries can vary up or down from optimum or rated voltage
Taps are provided on the designed Primary of the Transformer, usually located on the face of the coils of a Ventilated unit. The purpose of a tap is to provide the customer with connection points on the Primary coil so as to compensate for poor incoming/source voltage. Poor voltage is anything other than nominal and could be high or low. By utilizing a tap, it is possible for the customer to get an output from the Transformer that is close to it`s designed value. To intentionally over or under excite a Transformer by putting a significantly higher or lower voltage on a tap than it is rated can have a potentially catastrophic affect on the Transformer and is not supported by Square D/Schneider Electric.
CTA-ID : 2005512
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!