The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Buck Boost Transformers tend to work best with relative short wire runs.
Applies to SquareD/Schneider Electric Buck Boost Transformers
Resistance of wires in long wire runs causes a voltage drop that increases with the length of wire.
Since the load is not constant, the buck boost transformer is not a viable option. The voltage drop through the feeder conductors varies with the amount of current flowing through them. A buck boost is field connected to give a fixed percentage of voltage change. With a varying load, the customer could end up with too little voltage a the maximum load and too much voltage at the minimum load, either of which could be detrimental to the load(s).
The viable solution is to step up the voltage using either an isolation transformer or an autotransformer to transmit the electrical energy at as high a voltage possible to minimize the current, and hence minimize the voltage drop. Then use a second isolation transformer to step down the voltage at the point of use. Often, the second transformer may have primary taps which can allow for additional voltage correction at the load to maximize the performance of the overall system, while not presenting too high a voltage to the load equipment at the minimum loading. Contact Product Marketing/Support via the Field Office for support with issues of this nature.
CTA-ID : 2004653