Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
To do this you must have at least two pieces of information:
kVA = (V * I * 1.732) / 1000
where 1.732 is the simple numerical value for the square root of 3 (1.7320508...)
Then round up to the next standard 3ph kVA rating as found in Section 14 of SquareD/Schneider Electric Catalog, Digest 177.
Example: V = 208, I = 175; Therefore: kVA = (208 x 175 x 1.732) / 1000 = 63.05kVA
This calculates to 63+ kVA, thus we round up to 75kVA. From the Digest, a EX75T3H will satisfactorily serve this load.
Note: This is a simple kVA calculation and does not take into account possible special load requirements, such as found with motors or some medical equipment. For assistance, contact the Schneider Electric US Customer Care Center.