Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Voltages lower or higher than the range of available Buck Boost Calculators
Applies to Buck Boost Transformers by SquareD/Schneider Electric
Buck Boost Transformers offer a specific percentage of voltage increase or decrease, but within a set range
SquareD/Schneider Electric has a new Buck and Boost Transformer calculator which is available for use over the internet, or can be downloaded for use in a PDA (personal data assistant) via the link listed below.
Should the voltage drop below the listed value, the connection will still provide the same voltage ratio change (provided that the voltage does not drop below the point necessary to excite the core of the Transformer.) However, it is important to remember that a Transformer is a current rated device. Thus, the Autotransformer connection is current rated as well. So, if the voltage drops and the current rating remains fixed, then the overall kVA capacity of the Autotransformer connection drops proportionately.
CTA-ID : 2003001